title = "Reactive Power and Power Factor Requirements"

content = """
Grid codes mandate the reactive power range (or power factor range) that generators must
provide at the point of connection. This ensures adequate voltage support and stability
on the transmission system.

**Typical Ranges:** Gulf grid codes often require operation within a power factor band of
0.95 lagging to 0.95 leading, or equivalent reactive power in MVAr. The exact requirement
depends on the host grid and sometimes the plant size.

**Inverter Capability:** Inverters have a capability curve that defines the maximum reactive
power they can inject or absorb at a given active power level. Grid operations must ensure
that plant setpoints stay within both the grid code and equipment limits.

**TSO Requests:** TSOs may request specific reactive power setpoints for voltage support
during peak load, fault recovery, or other system conditions. These requests take precedence
over default operating modes.
"""  # noqa: E501

version = "0.0.1"
